During the process of green malt drying, raw material gelatinizing and saccharifing, wort boiling, beer fermenting, bottle pasteurizing, and sanitization in brewhouse, steam play an significant role.
Capacity : 2~25t/h
Fuel: Natural Gas, Lpg, Diesel, Hfo, Bunker Oil, Furnace Oil
WNS boiler is a safe and high efficiency (98%) heating equipment with high automation, it is fast assemble boiler with flue gas three pass and wet back structure, widely used for...
Fuel: wood chips, bagasse, straw, olive bone, coconut shell,peanut shell, pellets, rice husk and other biomass fuels
SZL series double drums boiler is horizontal type water tube boiler with high steam quality. The boiler adopts membrane water wall...
The price of beer boilers are based on the capacity and accessories. Generally, the accessories of boilers include burner/grate, electric controller, steam header, water softener, BFW pump, platform ladder, and chimney, etc. If you would like to use the specific devices (brand, materials, quantity, etc.) or the additional equipment (air preheater, economizer, condenser, etc.), the prices are quite different. So, if you would like to get the exact price, please inquire for the details.
1. Determine the capacity of the boiler. The boiler capacity should based on the Heating Load Curve or Heat Balance Diagram, and includes the heat loss in pipelines, self-used heat of boiler room, available used waste heat. While, usually, it is difficult to get the Heating Load Curve, the heating load could get based on the max thermal consumption per hour within production/heating/domestic, and then determine by using the coefficient.
2. Determine the heating supply medium. Generally, the brewery industry use the steam boiler for production. If there are large hot water demanded as well, both steam boiler and hot water boiler should be used.
3. Determine the boiler heating parameters, including pressure, temperature, etc.
4. Determine the boiler efficiency. In order to benefit for economic management, the boilers should have high thermal efficiency, and the boiler output, quantity and other performances have to adapt to the change of heat loading.
5. It’s better to select the boilers with same capacity or combustion equipment. If different, the max limitation is two models, to decrease the problems of equipment layout and management.